The Outdoor Telecom Cabinet is widely used in wireless communication base station, such as 3G system, communication/network integrated service, access/transmission switching station, emergency communication/transmission, etc.
The cabinet, made of hot dip galvanized steel, is a double wall cabinet with 20mm PEF insulation between inner plate and outer plate. The cabinet includes equipment compartments and battery compartments . It is easy for installation and with perfect sealing performance.
Equipment Compartment: The upper part of the cabinet is equipment compartment, which is separated with the battery compartment by division plate, for heat insulation of the equipment compartment.
Battery Compartment: The lower part of the cabinet is battery compartment, which is used for installing batteries.There’s heat insulation cotton between the cabinet inner wall and outer wall for keeping temperature. The cabinet includes air exhaust device for release of harmful air generated by the batteries.
Door and Door Lock: The cabinet door uses embedded structure. The door opening angle is larger than 110° and the door limit device can limit the opening angle. The lock is theftproof three point lock, supports padlock. There’s open door alarm sensor, which works together with the environment monitoring unit.
Cabinet Size : 1300mm×760mm×2150mm (W×D×H)
3.1 The cabinet is dustproof, sunproof and rainproof, which is suitable for outdoor environment.
3.2 The equipment compartment and battery compartment use air conditioner and fans for cooling, MTBF≥50000h.
3.3 -48V lamps is installed inside the cabinet.
3.4 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding. There’re entrance holes individually for power cable, signal cable and optical cable.
3.5 All the cables used in the cabinet are made from flame retardant materials.
4.7 Insulation Resistance: the insulation resistance between grounding devices and cabinet
body parts is not lower than 2X104M/500V(DC).
4.8 Withstand Voltage: the withstand voltage between grounding devices and cabinet body
parts is not lower than 3000V(DC)/1min.
4.9 Mechanical Strength: each surface can bear upright pressure＞980N; after the door is open, its outer end can bear upright pressure ＞200N.
Every compartment include a -48VDC lamp.
6.Environment Monitoring Unit
See the Annex 1 “Environment Monitoring Unit Manual”.
See the Annex 2 “ Air Conditioner Manual”.
8.Power Monitoring Module
See the Annex 3 “Power Monitoring Module Manual”.
9. Packing, Transport and Storage
The cabinet packing is damp proof and shock proof. The outside of the packing is painted with damp proof sign, shock proof sign, direction sign, etc.
The cabinet can be transported by various transportation ways. During the transportation, the environment temperature should be -30°C~+55°C, the relative humidity should be ≤90%(at +30°C). There should be a awning to prevent the product from rain and sunshine. Loading, unloading and moving of the product should be carried according to the transportation signs painted on the packing.
In the warehouse, the acid gas, Alkaline gas or other harmful gas should comply with the environment protection requirement.
TIANJIN ESTEL ELECTRONIC SCIENCE AND TECHNOLOGY CO., LTD