Payment & Shipping Terms:
|Cabinet Door:||1 Front Door||Layout:||1 Compartment|
|Certificates:||CE||External Size:||W×D×H 700*700*1000mm|
|Material:||Galvanized Steel||Color:||Grey / Optional|
|Cooling System:||Air Conditioner||IP Rating:||IP55|
IP55 Waterproof Corrosion Resistance Stainless Steel Outdoor Telecom Cabinet
1. Cabinet Overview
This small cabinet is made of 304 Stainless steel. It is Waterproof, dustproof, and corrosion resistance, provides flexible size options, offers the ideal enclosure solution to build the whole base station inside. The cabinet system can support Electrical equipments, Mornitoring system and etc.
2. Cabinet Specifications
|1||External dimensions||W*D*H 700*700*1000mm|
|2||Material||304 Stainless steel|
|3||Structure:||The insulation material is 20mm PEF|
|4||Cooling system||AC220V air conditioner|
|5||Heat Insulation||There are heat insulation on the outer wall.|
|6||Alarm Sensors||Water sensor, Door sensor, Smoke sensor, Temperature sensor and Humidity sensor|
|7||Lamp||DC48V LED lamp|
|9||Flame retardance||Comply with GB5169.7 test A|
|10||Temperature||Working Temperature:-40°C ~ +55°C|
|Storage Temperature:-50°C ~ + 70°C|
|Transport Temperature:-50°C ~ +70°C|
|11||Package||Wooden case with pallet|
3. Cabinet Features
3.1 External Dimension is W*D*H 700*700*1000mm
3.2 304 Stainless steel Material
3.3 Anti-theft three point lock
3.4 The cabinet includes 19” standard installation rack.
3.5 The cabinet cooling uses air conditioner
3.6 Including -48VDC illumination lamp.
3.7 The layout of the cabinet is reasonable, which will facilitate cable access, fixing and grounding.
3.8At the bottom of the cabinet, there are entrance holes individually for power cable, signal cable and optical cable.
3.9 The cabinet is dustproof, sunproof and rainproof, which is used in outdoor environment.
3.10 All the cables, sealing and heat insulation used in the cabinet are made from flame retardant materials, which comply with GB5169.7 test A
3.11 IP55 protection level.
4. Cabinet Cooling
One air conditioner with 1000W cooling capacity installed on the front door.
5. Cable Inlet
Feeder cable and other external cables all use bottom wiring method.
6. Grounding Protection
6.1The cabinet includes grounding copper bar with anti-corrosion coating. There are enough screws for wiring connection terminals.
6.2The metal part of the cabinet should be interconnected and be connected with grounding bar. Connection resistance between any two points is lower than 0.1Ω.
6.3Protective earthing of other equipments inside the cabinet should be connected to the grounding bar.
7. Quality Control
7.1Our company resolutely implements the principle of quality first, we control and supervise the whole production process in strict accordance with the requirements of the ISO9001 system and the related implementation process.
7.2The quality department strictly controls all aspects like material inspection, production processes, product testing, shipment inspection and establishes traceable documents and product identification.
7.3Our quality inspection team, is very familiar with the various standards, strict implementation of the standards required sampling and testing methods.