Sales & Support
Request A Quote - Email
Payment & Shipping Terms:
|External Dimension:||800*800*2000mm||Material:||Galvanized Steel; 1.5mm Thick Outer Plate, 0.8mm Thick Inner Plate|
|Door:||With One Front Door, And Anti-theft Three Point Lock For Outdoor Cabinet (support Padlock)||Ingress Protection:||IP55|
|Cooling:||Air Conditioner And Fans||Layout:||1 Bay|
Double Wall Air Conditioner Cooling Outdoor Telecom Cabinet With 19” Mounting Rack
1. Cabinet Instructions
This series cabinet is1800mm High and 800mm Wide and 800mm Deep. For those who need more than just standard cabinet, this series can also offer a truly the security of customized solution with lots of available options, providing a climate-controlled environment for any electronic equipment, electrical load panels and cable entry solutions. It provides a secure,climate controlled environment for any electronic equipment.
2. Cabinet Parameters
|Structure||Dimension||External Dimension: W*D*H 800*800*1800mm|
|Equipment Installation Method||19” rack|
|Door||With one front door, and special lock for outdoor cabinet (support padlock)|
|Material||Galvanized steel, 1.5mm thick outer plate, 0.8mm thick inner plate|
|Heat Insulation||There are heat insulation between inner wall and outer wall. The insulation material is 20mm PEF.|
|Structure||Welded or assembled|
|Temperature Control||Cooling||AC220V air conditioner and DC48V fans|
|Lighting||LED lamp||48V LED lamps (immovable), with protective circuit breaker|
|Temperature||Temperature||Working Temperature: -40°C ~ +55°C|
|Storage Temperature: -50°C ~ + 70°C|
|Transport Temperature: -50°C ~ +70°C|
|Humidity||Relative Humidity||5% ~ 100%|
|Pressure||Air Pressure||62kpa ~ 101kpa (similar to 0m ~ 5000m altitude)|
|Radiation Intensity||Solar Radiation Intensity||1120 ×(1±5%)W/m2|
4. Components Installation
4.1 LED lamp, smoke sensor and door sensor are installed at the top of the cabinet.
4.2 Air Conditioner and fans are installed on the door of the cabinet.
5.Cable Interal Pictures
(1) The cabinet includes grounding copper bar with anti-corrosion coating. There are enough screws for wiring connection terminals.
(2) The metal part of the cabinet should be interconnected and be connected with grounding bar. Connection resistance between any two points is lower than 0.1Ω.
(3)Protective earthing of other equipments inside the cabinet should be connected to the grounding bar.
7. Factory Introduction
Factory Size: 3000 Square Meters
No. of Main Production Lines: 5
Contract Manufacturing: OEM Service Offered, Design Service Offered, Buyer Label Offered
Production Experience: 13 Year