Sales & Support
Request A Quote - Email
Payment & Shipping Terms:
|IP Protection:||IP55||Cooling Capacity:||3000W|
3000W Cooling Capacity Kiosk Air Conditioner R134A Refrigerant With 1000W Heating Capacity
|Dimension and installation||Body outline dimension (width*height*depth )||mm||784*619*245|
Outline dimension including
|Installation method||Door Mounted|
|Environment and protection||Working environment temperature||℃||-40 to +55|
|Performance||Input voltage range||220 VAC±15% ～/50Hz|
|Rated Refrigerating input power(L35/L35)||W||1280|
|Rated Refrigerating current (L35/L35)||A||5.8|
|Maximum Refrigerating current||A||8.5|
|Air Volume of Inner Circulation||m3/h||900|
2.1 Removing package and checking
Please prepare installation tools: knife and scissors, and wear protective gloves.
Please remove wrapping film and packing belt, then remove the carton, take out the air conditioner.
Please check the attachment list and accessory bags in the carton, check whether the air conditioner model is right .
After removing the outer package, please make sure that the air conditioner is placed upright , and not placed horizontally or upside down.
After removing the outer package, please check carefully whether the appearance of the air conditioner is damaged or oil polluted, if the appearance of the air conditioner has obvious deformation or oil stain, please contact the manufacturer in time.
If there is no need to install the product immediately or it needs to be transported to other place, please repack the air conditioner after the checking.
It is recommended to recycle the unpacking materials.
2.2 Mechanical Installation
Installation tool: Phillips screwdriver
Choose cut location on the cabinet according to the holing diagram, remove the shadow area and make the installation hole.
Make air conditioner flange close to cabinet door, Fix the air conditioner on the installation surface of the cabinet firmly with M5 screws.
Check whether air conditioner is installed levelly and firmly.
Check whether air conditioner drainage loop is smooth, in case that drainage is blocked.
When determine the location of the installation hole in the cabinet, you should avoid the inlet and outlet air ports inside the cabinet are not blocked by any components inside the cabinet, and the two should be kept a horizontal distance of more than 150mm; otherwise, it is prone to lead to r short circuit of the return air, and poor cooling effect, etc.;
2.3 Electrical Installation
Power input port
|Live||L||power input cable L|
|Null||N||power input cable N|
|+ RS485 communication interface||RS485A||RS485 communication ports (+)|
|- RS485 communication interface||RS485B||RS485 communication ports (-)|